Vibration is a more common and more complex problem in the mechanical and electrical industry, for centrifugal pumps, when the vibration is too high, the analysis and summary are roughly the following situations:
The pipeline design is unreasonable, and the elbow of the import and export pipeline is too close to the pump, can cause pipe stress and turbulence,The picture is as follows:
2，轴承磨损或润滑不良。Bearing wear or poor lubrication.
There is a loose connection and loose fit, such as the coupling bolt is not locked, or the bearing lock nut is loose, or the bearing chamber is loose with the bearing.
When the water pump is installed, the alignment is not good, and the motor has soft feet.
The inlet filter screen is blocked, the inlet water is insufficient, the outlet back pressure is insufficient, the flow rate is too high, the pump is in overload operation, and the cavitation allowance is insufficient, resulting in large vibration caused by cavitation.
When the frequency conversion operation, there is ultra-high vibration at a specific frequency, and the pump and the motor vibrate greatly together, which may be a resonance phenomenon. What needs to be done is to change the frequency of operation or change the dynamic balance accuracy of the pump rotor, as well as change the rigidity of the structure, by grouting the base, welding reinforcement plate and other measures to change the frequency of the pump rotor itself.